Views: 6 Author: Site Editor Publish Time: 2018-02-01 Origin: Site
(1) The relevant capacitors should be tested and checked, and the reasons should not be found out, and the electric power is not allowed to be forcibly transmitted after the fuse is replaced;
(2) Pay attention to the standard of fuse installation and select the fuse with qualified quality;
(3) The fuse of the capacitor should be selected according to 1.37 ~ 1.50 times of the rated current of the capacitor to check whether the existing fuse meets the requirements;
(4) Increase the harmonic elimination device in the station to find out the cause of harmonic generation and improve it.