Views: 2 Author: Site Editor Publish Time: 2018-03-19 Origin: Site
There are many harmonic sources in the power network. If the harmonic is too large at the node of the shunt capacitor, if it is directly put into the shunt capacitor, it will often make the harmonic in the power network greater, and pose a great threat to the safety of the shunt capacitor.
The method of installing series reactor current limiting reactor XD1/2 can effectively restrain the occurrence of harmonic component and inrush current, and has obvious effect on ensuring the safe operation of shunt capacitor. The harmonic components in the installation of shunt capacitors should be tested in advance where conditions exist, and the capacity of the required series reactors should be determined according to the test results.
The installed capacity of the series reactor can also be determined directly according to the capacity of the installed shunt capacitor. In general, the harmonic at least 5 times should be selected by 6% of the capacity of shunt capacitor, and the harmonics of more than 3 times should be selected according to 12% of the capacity of shunt capacitor. In addition, in order to ensure the safe operation of shunt capacitors, the third harmonic amplification should be prevented in the places where the suppression of harmonic amplification is only more than 5 times (that is, the reactor capacity is the capacitance of the capacitor).
New energy vehicles, photovoltaics, wind power drive, film capacitor market has great potential
How to install low-voltage capacitors Installation precautions for low-voltage capacitors
What is a self-healing shunt capacitor -Working principle and application
How to measure whether the single-phase motor capacitor is good or bad
How to measure whether the starting capacitor of air conditioner compressor is good or bad？
The difference between starting capacitor and running capacitor of single-phase motor
How to measure whether the starting capacitor of air conditioner compressor is good or bad
Analysis on the selection and inspection method of compressor capacitor