Views:0 Author:Site Editor Publish Time: 2018-05-12 Origin:Site
6.The connection of individual compensation capacitors should be done: for induction motors that start directly or through a rheostat, the capacity of the power factor can be connected directly to the output terminals of the motor, and between the two. Three single-phase capacitors are adopted. Each capacitor is directly connected to the two terminals of each phase winding, so that the connection of the capacitor is always in accordance with the connection of the winding.
7.The packet compensated low voltage capacitors should be connected to the outside of the low voltage packet bus power switch to prevent the self excitation produced when the packet bus switch is disconnected.
8.The low voltage capacitor bank with centralized compensation shall be specially equipped with switches and installed on the outside side of the main switch instead of on the low voltage bus bar.